Nuisance, unpleasant or sometimes scary tripping of circuit breakers either local or up stream is a phenomenon which usually experienced or occurred when turning on a transformer especially with high capacity above 100kVA and low rated voltage below 600V. This is due the in born characteristic of a transformer that causes an inrush current with a high magnitude may be 10 to 18 times the rated current but in a very short duration to rush in to the transformer in the energizing phase.
Now, there is no more worry about this inrush current of transformer anymore. Because we provide a smart solution and answer to this matter.
The Soft Starter or Anti-Crash Device ACD is specially designed and built to eliminate this inrush current totally. It is very easy to install and operate. It is completely hassles free.
|Capacity||for transformer with capacity ranging from 100kVA to 2000kVA|
|Number of Phase||3 Phase|
|Operating Frequency||50Hz and 60Hz|
|Operating Voltage||200V, 208V, 220V, 380V, 400V, 415V, 440V, 480V|
|Function||To eliminate inrush current totally during turn on of transformer|
|Instrument||Operation indicating lamps|
|Termination||Heavy duty terminal block for use connection|
|Enclosure||Steel enclosure with powder coated finishing suitable for mounting in electrical distribution panel|
|Dimensions||240W x 175D x 360H (mm)|